Dear Label_Name,

Greetings! I hope you are well.

I am writing on behalf of an international publishing house, Science and Education Publishing, USA (http://www.sciepub.com).

Science and Education Publishing (SciEP) is a multidisciplinary open access publisher of Journals covering the fields of Science, Technology and Medicine. All SciEP publications are subject to high-quality peer review, editorial and production processes and are freely available online.

Welcome to the April, 2013 edition of SciEP newsletter, providing monthly summaries of articles on science & education related topics of interest to scientist and professionals. The mission of our journals is to provide an open access forum for publishing new findings on issues pertinent to scientific and academic field. We also invite you to submit original research papers, review articles, short reports, or case studies are considered for publication in our Multidisciplinary Journals.

American Journal of Public Health Research
DOI: 10.12691/ajphr-1-1-3

The Implementation of a Tele-Homecare System with Service Oriented Architecture and HL7 Message Transmission Standard
Ching-Sung Wang

American Journal of Medical and Biological Research
DOI: 10.12691/ajmbr-1-1-2

The Influence of Ethanol on Pyruvate Kinases Activity in Vivo, in Vitro, in Silico
Lelevich Sergey Vladimirovich, Khrustalev Vladislav Victorovich, Barkovsky Eugene Victorovich, Shedogubova Tatyana Aleksandrovna

American Journal of Medical Sciences and Medicine
DOI: 10.12691/ajmsm-1-1-1

Clinical and Histological Features in Wegener Granulomatosis
Li Cavoli Gioacchino, Passantino Rita, Bono Luisa, Tortorici Calogera, Ferrantelli Angelo, Giammarresi Carlo, Rotolo Ugo

American Journal of Infectious Diseases and Microbiology
DOI: 10.12691/ajidm-1-1-2

The Curse of Lymphatic Filariasis: Would the Continual Use of Diethylcarbamazine Eliminate this Scourge in Papua New Guinea?
Anne Lanham, Lillian Mwanri

We have released issues of some journals on February 2013.
American Journal of Public Health Research
American Journal of Medical Sciences and Medicine
American Journal of Medical and Biological Research
American Journal of Pharmacological Sciences
American Journal of Clinical Medicine Research
American Journal of Nursing Research
American Journal of Cancer Prevention
American Journal of Medicine Studies
American Journal of Infectious Diseases and Microbiology
American Journal of Cardiovascular Disease Research
American Journal of Biomedical Research
American Journal of Mechanical Engineering
American Journal of Microbiological Research
Journal of Preventive Medicine
American Journal of Food and Nutrition
American Journal of Hypertension Research
American Journal of Sports Science and Medicine
Journal of Cancer Research and Treatment
American Journal of Zoological Research
Journal of Biomedical Engineering and Technology
American Journal of Microbiological Research
Biomedical Science and Engineering

We are pleased to announce that submissions are now being accepted for peer review for all the journals across all our subject areas in SciEP.

Please submit your manuscript via our online submission system:
http://www.sciepub.com/author/signin

To unsubscribe from our mailing list, please click on the following link: unsubscribe

I am looking forward to hearing from you.

Kind regards,

David Rain
Email:join@sciepub.com
Science and Education Publishing (http://www.sciepub.com)

Pre-Feasibility Study for the Construction of a Photovoltaic Solar Power Plant with Energy Storage System Based on Lithium-Ion Batteries in Sub-Saharan Africa: Case of a 30 MWp Power Plant in Dapaong in Northern Togo

Kokou Prosper Semekonawo*, Bouwèreou Bignan-Kagomna, Oumarou Savadogo, Dramane Santara, Florent Xavier Nignan, Sié Kam, Joseph Dieudonné Bathiebo

Laboratoire d’Energies Thermiques Renouvelables, Université Joseph KI-ZERBO, 03 BP 7021 Ouagadougou 03, Burkina Faso

Abstract: The rate of access to electricity in Togo is estimated at 45% in 2018 despite the enormous solar potential with approximately 3203.1 hours that the country has. In order to remedy such a situation, the country plans, as part of its energy policy, to build a 30 MWp solar power plant with energy storage in Dapaong in northern Togo. In this article we propose a pre-feasibility study for the construction of the plant by addressing the technical, financial, environmental and social aspects. The construction of such a plant would require the installation of 112,320 solar panels of 275 Wp over an area of approximately 80 Hectares. We consider within the framework of this study, an energy storage duration of 2 h or 68 MWh thanks to the use of Lithium-ion batteries. The installation of this plant should require, according to our study, an investment of 82.4 million USD (50 billion XOF) with a cost of electricity produced by the plant of 0.16 USD/kWh (98.37 XOF/ kWh). This plant should make it possible to avoid an emission of around 30,749.76 tons of CO2 equivalent per year by producing clean electricity of around 42.7 GWh per year.

Keywords: photovoltaic solar power plant, energy storage, lithium-ion battery, dapaong, togo

Received September 09, 2023; Revised October 10, 2023; Accepted October 17, 2023

Citation: Kokou Prosper Semekonawo, Bouwèreou Bignan-Kagomna, Oumarou Savadogo, Dramane Santara, Florent Xavier Nignan, Sié Kam, Joseph Dieudonné Bathiebo, Pre-Feasibility Study for the Construction of a Photovoltaic Solar Power Plant with Energy Storage System Based on Lithium-Ion Batteries in Sub-Saharan Africa: Case of a 30 MWp Power Plant in Dapaong in Northern Togo. Sustainable Energy, 11 (1). 21-30. January 2023. doi:10.12691/rse-11-1-3

1. Introduction

A West African country with a population estimated at more than 8 million inhabitants in 2022, Togo is bound to the North by Burkina Faso, to the South by the Atlantic Ocean, to the East by Benin and to the West by Ghana. Like the majority of countries in sub-Saharan Africa, Togo has a very low electricity access rate of 45% in 2018 [1].

Moreover, in parallel with this low rate of access to electricity, the needs for electricity do not stop increasing, thus leaving the actors of the energy sector and the whole nation in a very complex situation to solve [2]. The most immediate solutions and generally seeming simpler are the installation of thermal power stations. Nevertheless, the use of such thermal power plants in a Togolese context would require enormous long-term costs due to the importation of fuels. Similarly, the emission of greenhouse gases at these power stations would have a very negative impact on the Togolese climate and the most visible of these impacts are floods and the rise in sea level causing an advance of the coasts (around 5 to 10 meters per year) [3].

Finally, it is necessary to find other types of power plants using the energy resources available on the Togolese territory and whose long-term operation is less expensive with a very low climatic impact [4].

Studies carried out to date indicate that in Togo, most of the potential energy resources are renewable energy resources, in particular hydraulics and solar energy. It therefore seems obvious to build hydroelectric and solar power plants exploiting the enormous potential of the various rivers, streams and the enormous solar field, to meet the electricity needs of the Togolese [5,6].

To achieve 100% access to electricity by 2030, the national electrification strategy obviously plans to increase the energy production base [7]. The increase in this production base is characterized by the installation of off-grid solar systems, the distribution of solar kits and the installation of large production plants. As for the share of renewable energies, it should normally accumulate a total capacity of 200 MW by 2020. As part of this energy policy, a 30 MWp photovoltaic solar power plant is planned in Dapaong in northern Togo. For the construction of this plant, the Togolese government will obtain funding under the RESPITE project (Regional Emergency Solar Power Intervention) approved by the World Bank on December 20, 2022 [8-9].

We propose through this article a prefeasibility study for the construction of this 30 MWp solar power plant with energy storage in Dapaong in northern Togo.

2. Technical Study for the Installation of the Plant

2.1. Choice of the Plant Site

Our choice of the site for the installation of the plant will essentially depend on the point of connection of the plant to the electricity transmission network, the obstacles (natural and unnatural obstacles) and the climatic data of the site.

2.1.1. The Injection Site

The power grid that will be used to transport the electricity produced by the power station must be located less than five (5) kilometers from the power station. In [10] Wu et al. identify standards that must be respected for PV integration to the grid. This measure aims to reduce power losses in transmission lines before injection into the grid. This measure is also recommended by international standards, in order to have better profitability for the plant.

Considering this fact, it seems wise to install the plant close (less than 5 km) to the Dapaong HTA/HTB transformer Power station. Thus, our plant would be installed within a maximum radius of 5 km from the Dapaong substation as shown on the CEET network map (Figure 1) [11].

Figure 1. Limit zone of electricity injection to the Dapaong HTA/HTB substation from the power station

2.1.2. The Obstacles

Uusing the Google Earth GIS software, we identified the various natural and unnatural obstacles within the radius of 5 km around the Dapaong HTA/HTB substation.

- Non-natural obstacles: These obstacles are essentially made up of large agglomerations such as villages, large infrastructures such as roads, public buildings, etc. They are represented in red color in Figure 2 and they are places not conducive to the establishment of the power plant;

- Natural obstacles: These obstacles are essentially mountains, forests, valleys, rivers, etc. It would be abnormal and, moreover, expensive to destroy such obstacles in order to set up a power station. These different obstacles are shown in green color in Figure 2. These are therefore places where it is not recommended to install our plant;

- Favorable sites: These sites represent favorable places with the minimum possible obstacles. They are represented in blue color in Figure 2 and they are places where, apart from the climatic characteristics (temperature and solar radiation especially), are advisable to install the plant.

Figure 2. Location of potential sites for the establishment of our power plant

Ø Zone 1: It represents a natural obstacle. It is in reality simply the Lions' Den National Park. A closer view as in the following Figure allows us to better understand the area dominated by a large number of flora and fauna.

Figure 3. Zone 1

Ø Zone 2: It also represents a natural obstacle. It is in reality the Dapaong’s Dam. A closer view allows us to better see this dam and its water resources.

Figure 4. Zone 2

Ø Zone 3: It also represents a natural obstacle. It is a mountainous area with hills. The following Figure shows the state of this area more clearly.

Figure 5. Zone 3

Ø Zone 4: It has its level, represents an unnatural obstacle. This area simply represents the downtown area of Dapaong City. This is the area bringing together the largest urban area of the city of Dapaong. A closer view allows you to better understand buildings, roads, etc.

Figure 6. Zone 4

Ø Zone 5: Of all the selected zones, this represents the zone with the fewest natural and unnatural obstacles. A closer view shows that it is an area characterized by relocated buildings and very few, tracks for the movement of people and some trees. We consider this area ideal for the installation of our power plant. For those who are few of the populations residing in this area, the government should therefore find them other sites on which they can locate themselves without worries and which will also be able to facilitate their various activities as on the site of yesteryear.

Figure 7. Zone 5

Figure 8. Variation curve of the solar irradiation of zone 5 between 2007 and 2016

Table 1. Global solar radiation on a horizontal plane of Zone 5 between 2007 and 2016

Table 2. Temperature variation in Zone 5 between 2007 and 2016

Figure 9. Curve of temperature variation in zone 5 between 2007 and 2016

2.2. Solar Resource of the Site

By locating zone 5 on PVGIS, we obtained the solar radiation and temperature data over a period of ten (10) years, i.e. from 2007 to 2016 (view Table 1 & Table 2) [12]. Thus, by taking an average over these ten years, the solar irradiation is 2066.8 kWh/m²/year and the average temperature is 27.64°C. Figure 8 & 9 and Table 1 & 2 illustrate these climate data from PVGIS.

2.3. Sizing of the Solar Power Plant

2.3.1 Choice of Solar Power Plant Inverters

Given that our plant will be made with a storage system, so in the context of this study, we will consider two (2) types of inverters: the inverter intended for the conversion of the energy of the PV panels (P_inv) and those intended for the conversion of the energy of the storage system (S_inv).

Ø The P_inv inverter: For this study the P_inv characteristics that we considered are as follows in Table 3:

Table 3. Characteristics of the P_inv type inverter

Ø S_inv inverter: For this study the S_inv characteristics that we considered are as follows in Table 4:

Table 4. Characteristics of the S_inv type inverter

2.3.2. Sizing of a Solar Panel Shed

The evaluation of the powers, currents and voltages at temperatures different from those of the STC (Standard Test Conditions) are given by the following relationships [13,14,15]:

Ø For power, we have:

[picture] | (1)

Ø For voltage, we have:

[picture] | (2)

Ø For the current, we have:

[picture] | (3)

K p , K v , K i are respectively the temperature coefficients of the power, voltage and current of the PV panel. T and TSTC are respectively the temperature of the installation site of the plant and the temperature of STC conditions for the manufacture of the solar panels.

For the sizing of Sheds, the following conditions must be respected [16,17].

[picture] | (4)

[picture] | (5)

[picture] | (6)

[picture] | (7)

[picture] | (8)

[picture] | (9)

[picture] | (10)

[picture] | (11)

[picture] | (12)

[picture] | (13)

With Vcoss the short-circuit voltage of the sub-shed, Vmpss the voltage at the maximum power point of the sub-shed, Pss the total peak power of the sub-shed, Iccss the short-circuit current of the sub-shed, Impss the current at the maximum power point of the sub-shed, Nps the number of panels per string of the sub-shed, Npss the number of panels per sub-shed and Nsss the number of strings per sub-shed.

Table 5. Configuration of a Shed of PV panels

2.3.3. Overall Configuration of the PV Panels of the Plant

By associating several sheds and taking into account that the plant we want to install is 30 MWp, we can make the overall Configuration of the plant, thus allowing us to know for our plant, the number of inverters to be installed, the total number solar panels to be installed.

In summary, the global Configuration data of the plant are as follows in Table 6:

Table 6. Global plant Configuration data

2.3.4. Plant storage System Configuration

To have continuous production on the electrical network even in periods of low sunshine, a storage time (Ts) of 2 hours is planned for our plant. The system chosen for our plant is electrochemical storage with lithium-ion technology.

Since the field of photovoltaic panels is subdivided into a shed, the storage system to store the surplus energy produced by its solar panels would also be configured in a shed.

2.3.4.1. Configuration a Shed Storage System

The sizing of the shed storage system is based on the characteristics of the PV shed and the characteristics of the battery. For this sizing, we will consider [18,19,20]:

Ø Ems the minimum energy storage system needed. With:

[picture] | (14)

Ø Nmse the maximum number of batteries in series per input. With:

[picture] | (15)

Ø Vmie the nominal voltage of the battery pack per input. With:

[picture] | (16)

Ø Vmae the maximum battery pack voltage per input. With:

[picture] | (17)

Ø Eps the battery pack energy per input. With:

[picture] | (18)

Ø Ne the entry number. With:

[picture] | (19)

Ø Es the energy stored by inverter. With:

[picture] | (20)

Ø Cts the capacity of the storage system per inverter. With:

[picture] | (21)

Ø Nts the total number of batteries per shed. With:

[picture] | (22)

Nevertheless, in order to ensure optimal operation of the storage system, the inverter input voltage range must be compatible with the end-of-charge (Vmae) and end-of-discharge (Vmie) voltages of the storage system. Which means:

[picture] | (23)

[picture] | (24)

Table 7. Shed storage system Configuration data

2.3.4.2. Overall Configuration of the Plant Storage System

Based on the per-shed Configuration of the storage system, we can perform the overall Configuration of the storage system. We will consider [21,22,23]:

Ø Egs the overall energy of the storage system. With:

(25)

Ø Ct the overall capacity of the storage system. With:

(26)

Ø Nt is the total number of batteries in the storage system. With:

(27)

Ø Nshed the total number of shed.

Table 8. Storage system global Configuration data

Table 9. Plant installation area

2.4. Installation Area of the Plant

Taking into account the dimensions of the PV panels, the storage system and the respect of the shade between the different rows of PV panels, we determined the active surface (i.e. the surface which produces electricity) and the total area (i.e. the total area to be fenced) of the plant.

Figure 10. Overall presentation of the PV plant

Figure 11. Variation in the energy produced by the plant during the year

2.5. Electrical Cables and Protections of the Plant

In this part we will evaluate the section of the electrical conductors which connect the different components of the power plant.

This evaluation of conductor cross-section depends on the length of the conductor, the maximum current to flow in the conductor, the resistivity of the conductor and the maximum acceptable voltage drop over the entire length of the conductor [24]. This minimum section is expressed by the following relation (28):

[picture] | (28)

For the protection of people and property, fuse holders, thermal magnetic circuit breakers, differential circuit breakers and lightning arresters must be installed between the various components of the plant. One or more lightning rods must also be installed to protect the plant equipment against thunder.

Table 10. Conductor section between plant components

2.6. Plant Performance and Productivity

The power plant suffers energy losses at all levels, that is to say from the solar panels to the output of electricity for the distribution of energy. We have evaluated and summarized these losses in the following Table (Table 11):

Table 11. Different losses between plant components

Table 12. Electricity production during the year by the plant

Taking into account the solar irradiation of the site (En), the active surface of the solar panels (SA) and the overall efficiency of the installation (ηG), the energy produced by the plant can be evaluated by the relationship (29):

[picture] | (29)

In Figure 11, it appears that the most productive month is March with a monthly production of 4.08 GWh/month and the least productive month is August with a monthly production of 2.843 GWh/month.

The annual energy produced by the plant is the sum of the monthly energy produced by the plant. It can be evaluated as follows:

[picture] | (30)

Ep = 42.708 GWh /year

Also called Yield, the productivity of the plant makes it possible to estimate the annual operating time of the plant taking into account the nominal operating conditions of the components of the plant. It is expressed in peak hours per year (hc/year) and is assessed by calculating the ratio between the annual energy produced by the plant and the total peak power installed. In the case of our plant, it is evaluated as follows in relationship (31):

[picture] | (31)

Pd = 1382.67 hc/year

Thus, we can consider that our plant will operate under its nominal power of 30.888 MWp for 1382.67 hours per year.

3. Economic Studies

The investment cost of the plant is assessed taking into account the cost of equipment and its installation and the cost of connection to the electricity network.

Thus, the total investment cost of the plant is evaluated as:

CI = 82,432,511 USD = 49,892,277,299 XOF

The operating cost of the plant includes the cost of annual maintenance (which in the standards must not exceed 1% of the cost of installation) and the cost of paying staff. Thus, the operating cost of the plant is evaluated at:

CE = 1,002,764 USD = 606,922,773 XOF

Still called Levelized Cost of Energy, the cost of the electricity produced by our plant is determined by dividing the overall cost of the investment and operation of the plant by the total energy produced by the plant [25]. It is therefore evaluated by the following relationship (32):

[picture] | (32)

With A, the annuity factor calculated as follows:

[picture] | (33)

With:

Ø n the lifespan of our plant, which we take at 25 years;

Ø Kd the interest rate which would be taken at 6%;

Ø Ka the insurance rate that would be taken at 0.5%.

A = 0.0832

Thus, the cost of electricity from our plant is:

LCE = 0.16 USD/kWh = 98.37 XOF/kWh

4. Environmental Impact Study of the Plant

It is no longer a secret nowadays that solar panels help protect the environment by avoiding the emission of greenhouse gases responsible for global warming. Therefore, our plant will not be an exception since its major components are solar panels.

Thus, taking into account the Greenhouse Gas Emission Factor (GEF) in Togo [26] which is 0.72 eqkgCO2 /kWh, the annual energy produced by the plant (Ep) and the lifetime of the plant (n i.e. 25 years), we will evaluate the quantity of greenhouse gases (QCO2ev) avoided by our plant as follows:

[picture] | (34)

QCO2ev = 768,744 eqCO2 avoided

QCO2ev = 30,749.76 eqCO2 avoided per year

Using the RETScreen software, we will evaluate the equivalent of this quantity of greenhouse gases from our plant and which is:

Qbaril = 71,512 barrels of oil not consumed per year

Qplant = 2,828 Hectares of forest absorbing carbon per year

From the design of their various components to their construction on a given site, photovoltaic solar power plants have an impact on the environment. In the case of our project, we can cite some impacts:

• The industries producing the components of a solar power plant produce enormous quantities of Greenhouse Gases during the production of these components. In addition, these component production industries not being on the installation site of the power plant, then it will be necessary to ensure the transport of these components to the installation sites of the power plant and which also constitutes a significant source of environmental pollution. Generally known as the carbon debt for the case of solar panels, it is estimated that the pollution mentioned above would be reimbursed by the panels after two (2) or three (3) years of operation of the installation [27];

• The installation of the plant in zone 5 constitutes in a way, a small source of deforestation. In the sense that before the establishment of the plant, there were some trees on the site (visible on the image of Google Earth) and these trees would be cut down to be able to set up the plant;

• Before the establishment of the power plant, there existed on the site a certain fauna quite at ease in its biocenosis, but the establishment of the power plant risks modifying or even eliminating this biocenosis;

• In a Togolese context, the recycling of components (especially solar panels and batteries) of the plant at the end of its lifespan is not yet possible. So the question remains to know what would become this waste if we know the chemicals that compose it and especially the impact of these products on the environment (soil, air, water etc.)

5. Social Impact Study of the Plant

The establishment of this plant has many positive impacts on the social level, among which we can cite:

• The creation of temporary jobs during construction periods and permanent jobs during plant operation periods. Even if these jobs may seem insignificant, they could have a significant effect on the unemployment rate which remains high in Togo;

• Access to electricity has many advantages for populations. And this would also be the case for the populations who will benefit from the electrical energy produced by our plant;

• For local populations, many income-generating activities could arise from the establishment of the plant in their area;

• The establishment of such a large-scale infrastructure would require the creation of other infrastructures such as roads, a hospital, etc., which would contribute to a significant improvement in the standard of living of the local populations.

6. Conclusion

This study aims to propose a pre-feasibility study of the installation of a 30 MWp solar power plant with Lithium-ion battery-based energy storage (with a total capacity of 68 MWh). This study addresses the technical, economic, social and environmental aspects related to the construction of such a plant. But this study remains nevertheless, a brushed study and more in-depth studies could be carried out in order to be able to carry out the power plant.

7. Source of Funding

This research has not received any specific grants from funding agencies in the public, commercial, or not-for-profit sectors.

References

[1]   | GIZ, Approvisionnement en énergie décentralisée au Togo (ProENERGIE), 2019.
[2]   | Kokou Prosper Semekonawo, Modèles de réseaux de neurones artificiels LSTM, ARIMA et de régression multivariable pour une analyse prévisionnelle de la demande d’énergie électrique en Afrique de l’Ouest, Université Joseph KI-ZERBO, PhD Thesis, 2023.
[3]   | Pierre OZER, Yvon-Carmen HOUNTONDJI, Florence DE LONGUEVILLE, Recent evolution of the coastline in the Bight of Benin. Example of Togo and Benin, 2017.

[4]  
Amega Kokou, Yendoubé Laré, Ramchandra Bhandari, Yacouba Moumouni, Aklesso Y. G. Egbendewe, Windmanagda Sawadogo, and Saidou Madougou, Solar Energy Powered Decentralized Smart-Grid for Sustainable Energy Supply in Low-Income Countries: Analysis Considering Climate Change Influences in Togo" Energies 15, no. 24: 9532, 2022.

[5]   | Todine Salifou, Amy Nabiliou, Mataani F. Alloula, Juzer Vasi, Philippe Malbranche, Heinz Ossenbrink, Pierre Verlinden, Stefan Nowak, Sarah Kurtz, Lawrence L. Kazmerski, Creating a solar roadmap for the Republic of Togo, Solar Compass, Volume 6, 2023.
[6]   | chilabalo E. Patchali, Olusegun O. Ajide, Olaniran J. Matthew, T.A.O. Salau, Olanrewaju M. Oyewola, Generation of meteorological year for the assessment of photovoltaic systems performance in Togo, West Africa, Scientific African, Volume 16, 2022.
[7]   | AT2ER, Stratégie d’électrification du Togo, 2018.
[8]   | World Bank, World Bank Approves $311 Million to Increase Grid-Connected Renewable Energy Capacity in West Africa, , December 2022.
[9]   | World Bank, Procurement details, , 2022.
[10]   | Yuan-Kang Wu, Jhih-Hao Lin, Huei-Jeng Lin, Standards and Guidelines for Grid-Connected Photovoltaic Generation Systems: A Review and Comparison, IEEE Transactions on Industry Applications, 53(4), 3205–3216, 2017.
[11]   | ARSE, «Rapport d’activité 2017», 2018.
[12]   | PVGIS, Photovoltaic geographical information system , 2023.
[13]   | Mesude Bayrakci, Yosoon Choi, Jeffrey R. S. Brownson, Temperature Dependent Power Modeling of Photovoltaics, Energy Procedia, 57 (2014) 745-754, 2013.
[14]   | I. Mustapha, B. U. Musa, M. K. Dikwa, M. Abbagana, Electrical parameters estimation of solar photovoltaic module, Journal of Engineering and Applied Science, 2022.
[15]   | Dubey B., Tiwari D., Kumar R., Effect of temperature variations over Photovoltaic modules efficiency of different technologies at NOCT, IEEE Students’ Conference on Electrical, Electronics and Computer Science (SCEECS), 2016.
[16]   | E. A. Setiawan, A. Setiawan, D. Siregar, Analysis on solar panel performance and pv-inverter Configuration for tropical region, Journal of Thermal Engineering, Vol. 3, No. 3, pp. 1259-1270, 2017.
[17]   | Rupendra Kumar Pachauri, Om Prakash Mahela, Abhishek Sharma, Jianbo Bai, Yogesh K. Chauhan, Baseem Khan, Hassan Haes Alhelou, Impact of Partial Shading on Various PV Array Configurations and Different Modeling Approaches: A Comprehensive Review, IEEE Power & Energy Society Section, 2020.
[18]   | Rehman S., Ahmed M. A., Mohamed M. H., Al-Sulaiman F. A, Feasibility study of the grid connected 10 MW installed capacity PV power plants in Saudi Arabia, Renewable and Sustainable Energy Reviews, 80, 319–329, 2017.
[19]   | Hussein A. Kazema, M.H. Albadib, Ali H.A. Al-Waelic, Ahmed H. Al-Busaidid, Miqdam T. Chaichane, Techno-economic feasibility analysis of 1 MW photovoltaic grid connected system in Oman, Case Studies in Thermal Engineering, 2017.
[20]   | Al-Sabounchi A. M., Yalyali S. A., Al-Thani H. A., Design and performance evaluation of a photovoltaic grid-connected system in hot weather conditions, Renewable Energy, 53, 71–78, 2013.
[21]   | Rallabandi V., Akeyo O. M., Jewell N., Ionel D. M, Incorporating Battery Energy Storage Systems into Multi-MW Grid Connected PV Systems, IEEE Transactions on Industry Applications, 1–1, 2018.
[22]   | Jianlin Li, Yushi Xue, Liting Tian, Xiaodong Yuan, Research on optimal Configuration strategy of energy storage capacity in gridconnected microgrid, Protection and Control of Modern Power Systems, 2017.
[23]   | Gaztanaga H., Landaluze J., Etxeberria-Otadui I., Padros A., Berazaluce I., Cuesta D., Enhanced experimental PV plant grid-integration with a MW Lithium-Ion energy storage system, IEEE Energy Conversion Congress and Exposition, 2013.
[24]   | Koami S. Hayibo, Joshua M. Pearce, Optimal inverter and wire selection for solar photovoltaic fencing applications, Renewable Energy Focus, 42, Pages 115-128, 2022.
[25]   | Chun Sing Lai, M.D. McCulloch, Levelized Cost of Energy for PV and Grid Scale Energy Storage Systems, Energy and Power Group, Department of Engineering Science, University of Oxford, UK, 2016.
[26]   | Kokou Sabi, Akpe Agbossou, Abiziou Tchinguilou, Zikpo Fo-Me, Ayassou Koffi, Carbon intensity of the energy sector for togo in 2012, Global Journal of Pure and Applied Sciences Vol. 23, 2017: 367-375, 2017.
[27]   | Pinto M. A., Frate C. A., Rodrigues T. O., Caldeira-Pires A., Sensitivity analysis of the carbon payback time for a Brazilian photovoltaic power plant, Utilities Policy, 63, 101014, 2020.