Dear Label_Name,

Greetings! I hope you are well.

I am writing on behalf of an international publishing house, Science and Education Publishing, USA (http://www.sciepub.com).

Science and Education Publishing (SciEP) is a multidisciplinary open access publisher of Journals covering the fields of Science, Technology and Medicine. All SciEP publications are subject to high-quality peer review, editorial and production processes and are freely available online.

Welcome to the April, 2013 edition of SciEP newsletter, providing monthly summaries of articles on science & education related topics of interest to scientist and professionals. The mission of our journals is to provide an open access forum for publishing new findings on issues pertinent to scientific and academic field. We also invite you to submit original research papers, review articles, short reports, or case studies are considered for publication in our Multidisciplinary Journals.

American Journal of Public Health Research
DOI: 10.12691/ajphr-1-1-3

The Implementation of a Tele-Homecare System with Service Oriented Architecture and HL7 Message Transmission Standard
Ching-Sung Wang

American Journal of Medical and Biological Research
DOI: 10.12691/ajmbr-1-1-2

The Influence of Ethanol on Pyruvate Kinases Activity in Vivo, in Vitro, in Silico
Lelevich Sergey Vladimirovich, Khrustalev Vladislav Victorovich, Barkovsky Eugene Victorovich, Shedogubova Tatyana Aleksandrovna

American Journal of Medical Sciences and Medicine
DOI: 10.12691/ajmsm-1-1-1

Clinical and Histological Features in Wegener Granulomatosis
Li Cavoli Gioacchino, Passantino Rita, Bono Luisa, Tortorici Calogera, Ferrantelli Angelo, Giammarresi Carlo, Rotolo Ugo

American Journal of Infectious Diseases and Microbiology
DOI: 10.12691/ajidm-1-1-2

The Curse of Lymphatic Filariasis: Would the Continual Use of Diethylcarbamazine Eliminate this Scourge in Papua New Guinea?
Anne Lanham, Lillian Mwanri

We have released issues of some journals on February 2013.
American Journal of Public Health Research
American Journal of Medical Sciences and Medicine
American Journal of Medical and Biological Research
American Journal of Pharmacological Sciences
American Journal of Clinical Medicine Research
American Journal of Nursing Research
American Journal of Cancer Prevention
American Journal of Medicine Studies
American Journal of Infectious Diseases and Microbiology
American Journal of Cardiovascular Disease Research
American Journal of Biomedical Research
American Journal of Mechanical Engineering
American Journal of Microbiological Research
Journal of Preventive Medicine
American Journal of Food and Nutrition
American Journal of Hypertension Research
American Journal of Sports Science and Medicine
Journal of Cancer Research and Treatment
American Journal of Zoological Research
Journal of Biomedical Engineering and Technology
American Journal of Microbiological Research
Biomedical Science and Engineering

We are pleased to announce that submissions are now being accepted for peer review for all the journals across all our subject areas in SciEP.

Please submit your manuscript via our online submission system:
http://www.sciepub.com/author/signin

To unsubscribe from our mailing list, please click on the following link: unsubscribe

I am looking forward to hearing from you.

Kind regards,

David Rain
Email:join@sciepub.com
Science and Education Publishing (http://www.sciepub.com)

A Contribution to the Insulating System State Estimation for Power Transformers Installed in Amman - Jordan

khalaf Y. Alzyoud

Electrical Engineering Department, Faculty of Engineering Technology, Al-Balqa Applied University, Amman, Jordan

Abstract: This work focus on observation of the insulating system and analysis of the insulation resistance measurement results in 110kV, 20 and 63 MVA oil-immersed power transformers are presented. The observation was undertaken from the start-up and it includes graphical and numerical values obtained by measurements, the analysis of the state of insulation provides possibilities to undertake remedial action in due time with the aim to extend the transformer life.

Keywords: contribution, transformer, estimation, insulation, oil transformer

Citation: khalaf Y. Alzyoud, A Contribution to the Insulating System State Estimation for Power Transformers Installed in Amman - Jordan. American Journal of Electrical and Electronic Engineering, 6 (1). 28-31. January 2018. doi:10.12691/ajeee-6-1-4

1. Introduction

The power transformer represents one of the most important functional components of a power facility, In addition, taking into account the development of electric machines the transformer happens to be among the very first to be developed, Under operating conditions its life extends to about 30 years, Observation of its functional behavior during its life offers important data that may be used as a basis for improvement of its design, technology, for intermediate action under operating conditions all with the aim to extend its life, Generally speaking the transformer represents a complex unit consisting of the following fundamental systems: conductive system - magnetic system- insulating system -supporting system (structure) -protective system.

Each of these systems represents an important and inseparable part with respect to the transformer as a whole. Besides, analysis of its component parts proves to be an interesting experience. Each of the complex system mentioned above includes several subsystems that deserve special consideration and attention. ln this paper, the insulation system is presented. This system plays key role in the functioning of the unit and due to its sensitivity and complexity it requires very close consideration as to its design and engineering and technological aspects. Observation of the insulating system by means of selected methods (insulation testing by means of a mega ohmmeter) over a number of years gives a general idea of the insulation state, roughly speaking, the insulating system can be divided into:

Bushings (porcelain) -oil part - cellulose (paper, wood) part - coating-resins (sheet metal, winding.) - Geometry (gaps).

2. Research Method

The following methods have been used for observation of the insulation ageing - Current-voltage measurements (a method)-inductor measurements (mega ohmmeter)-ultrasonic measurements-winding loss angle measurements-chemical analysis, chromatography - capacitance and inductivity measurements. Enclosed in the paper is the figure showing the insulating system observed by a single method over a given period of years. We have selected the inductor measurement method of observation for presentation of the insulating system. This method is known for its adaptability to the operating conditions, fast procurement of results, simple instruments and mobility. This method provides a general idea of the insulation system state. The diagrams and tables show the state of insulating system for five (5), 110/35/10kV, 20 and 63 MVA transformers. These results have been reduced to 20C temperature and they refer to transformers in operation exposed to all conditions that normally happen in a network (over voltages, short-circuits, fluctuation of load, etc.) including all lightning phenomena. Figure 1 illustrates in the best way the behavior of insulation resistance on a transformer in which the insulation level decreased after the commissioning in the factory.

As shown in Figure 2 the permanent decline of insulation, there is no improvement after energizing the transformer either as shown on Figure 3, for MV and LV- Ground. Experience related to other transformers show that an improvement would normally occur after setting the transformer into operation. This is probably due to the elimination of the residual humidity from the system.

Figure 1.

Figure 2.

Figure 3.

Figure 4.

Figure 5.

Figure 3 shows continuous decline of insulation resistance which can be explained by insufficient loading and oil heating (drying) after the start-up which did not allow any significant improvement to occur. A transformer which managed to maintain its insulating properties on a permanent level over a 17-year period of operation because it functioned under nearly nominal conditions as shown in Figure 4

Figure 5 shows a transformer in which a deviation from its characteristics of R15 and R60 for HV and MD-Ground took place. These deviations could be most probably attributed to measurement errors. After one year, the transformer was energized immediately after the installation and over a period of. four subsequent years continuous improvement of the insulation resistance took place, After these, there. came a period of expected decline of insulation properties as a result of the normal ageing process It must be emphasized that measurement method provides approximate results that night serve for the insulation state estimation although it has been strongly influenced by wither conditions, by the fact , , that different measuring instruments were used, by the precision of readings, etc. The observation carried out provides interesting data which proved that such observations are useful and important. In order to obtain a general state estimation it is required to carry out the observations during the entire life of the transformer, This approach enables procurement of data which can be used as a guide for necessary steps that are needed to slow down the ageing process and extension of the transformer useful life.

3. Results and Analysis

Table 1 illustrate the Transformer: o1 "Amman, 110/33/11KV 20 MVA, the insulation resistance has been reduced to 20c0 temperature.

Table 1. Transformer: "Jo1" Amman

Table 2 shows the Transformer: "Jo2" Amman, 110/33/11KV 63 MVA, insulation resistance has been reduced to 20c0 temperature

Table 2. Transformer: "Jo2" Amman

Table 3. Transformer: "Jo 3" Amman

Table 4. Transformer: "Jo 4" Amman TDRN3XC _16000/110, 110/2X10/10KV 20 MVA

Table 5. Transformer: "Jo 5" _ Amman TDR 3XC _16000/110, 110/10/10KV 20 MVA

4. Conclusion

The observation and analysis of insulation under operating conditions is of utmost importance. The observation results allow to carry out insulation state estimation and to predict future tendencies in its behavior. They also provide basis for defining necessary steps and remedial action aimed at extension of transformer useful life. Among other things, the results reflect the quality of insulating materials used; The following advantage is the possibility to plan auxiliary transformer requirements in cases when accelerated decline of insulation becomes evident. The data concerning the state of insulation may become important background data for new transformer developments.

References

[1]   | “IEEE Std C57.12.90-1999”, IEEE Standard Test Code for Liquid Immersed Distribution Power and Regulating Transformer.
[2]   | “Measurement of relative permittivity dielectric dissipation factor and, d.c. resistivity of insulating liquids”, IEC 60247.
[3]   | Wang, M., Vandermaar, A.J., and Srivastava, K.D., “Review of condition assessment of power transformers in service,” IEEE Electr. Insulat. Mag.,, Vol. 18, pp. 12-25, 2002.
[4]   | Singh, J., Sood, Y.R., and Verma, P., “Experimental investigation using accelerated aging factors on dielectric properties of transformer insulating oil,” Electr. Power Compon. Syst., Vol. 39, pp.1045-1059, 2011
[5]   | Shroff, D.H., and Stannett, A.W., “A review of paper ageing in power transformers,” Proc. IEE, Vol. 132, pp. 312-319, 1985.
[6]   | T. X. Xue, B. Xie, and Y. Lu: Study on The Insulation Life Models Of Power Transformer “, IEEE, 2008.
[7]   | W Young, Transformer life management- condition monitoring, Proceedings of the 1998 IEE Colloquium on transformers life, IEE Colloquium(Digest)IEE Stevange, Engl, p2/1-2/4
[8]   | Romero, A.A., Mombello, E.E. and Rattá, G., An overview on power transformer management: Individual assets and fleets, Transmission and Distribution Latin America Conference and Exposition (T&D-LA), Sixth IEEE/PES, pp. 1-7, 2012.
[9]   | Susa, D. and Nordman, H., A simple model for calculating transformer hot spot temperature, IEEE Transactions on Power Delivery, 24(3), pp. 1257-1265, 2009.
[10]   | CIGRE, Moisture equilibrium and moisture migration within transformer insulation systems, Vol. A2.30, Ed, 2008.
[11]   | Fofana, I., Borsi, H. and Gockenbach, E., Fundamental investigations on some transformer liquids under various outdoor conditions, IEEE Transactions on Dielectrics and Electrical Insulation, 8(6), pp. 1040-1047, 2001.
[12]   | Gelegenis, J.J., Estimation of hourly temperature data from their monthly average values: case study of Greece, Renewable Energy, 18(1), pp. 49-60, 1999.
[13]   | Gomez-Luna, E., Duarte, C., Aponte, G., Guerra, J.P. and Goossen, K.W., Experiences with non-intrusive monitoring of distribution transformers based on the on-line frequency response, Ingeniería e Investigación, 35(1) , pp. 55-59, 2015.
[14]   | Crine J.P.; “On the interpretation of some electrical aging and relaxatio phenomena in solid dielectrics”, IEEE Transactions on Dielectrics and Electrical Insulation, 2005, Vol. 12, No.6, pp.1089-1107.
[15]   | Muthanna K.T., Sarkar A., Das K., Waldner K.; “Transformer insulation life assessment”, IEEE Transactions on Power Delivery, 2006, Vol. 21, No. 1, pp. 150-156.