Dear Label_Name,

Greetings! I hope you are well.

I am writing on behalf of an international publishing house, Science and Education Publishing, USA (http://www.sciepub.com).

Science and Education Publishing (SciEP) is a multidisciplinary open access publisher of Journals covering the fields of Science, Technology and Medicine. All SciEP publications are subject to high-quality peer review, editorial and production processes and are freely available online.

Welcome to the April, 2013 edition of SciEP newsletter, providing monthly summaries of articles on science & education related topics of interest to scientist and professionals. The mission of our journals is to provide an open access forum for publishing new findings on issues pertinent to scientific and academic field. We also invite you to submit original research papers, review articles, short reports, or case studies are considered for publication in our Multidisciplinary Journals.

American Journal of Public Health Research
DOI: 10.12691/ajphr-1-1-3

The Implementation of a Tele-Homecare System with Service Oriented Architecture and HL7 Message Transmission Standard
Ching-Sung Wang

American Journal of Medical and Biological Research
DOI: 10.12691/ajmbr-1-1-2

The Influence of Ethanol on Pyruvate Kinases Activity in Vivo, in Vitro, in Silico
Lelevich Sergey Vladimirovich, Khrustalev Vladislav Victorovich, Barkovsky Eugene Victorovich, Shedogubova Tatyana Aleksandrovna

American Journal of Medical Sciences and Medicine
DOI: 10.12691/ajmsm-1-1-1

Clinical and Histological Features in Wegener Granulomatosis
Li Cavoli Gioacchino, Passantino Rita, Bono Luisa, Tortorici Calogera, Ferrantelli Angelo, Giammarresi Carlo, Rotolo Ugo

American Journal of Infectious Diseases and Microbiology
DOI: 10.12691/ajidm-1-1-2

The Curse of Lymphatic Filariasis: Would the Continual Use of Diethylcarbamazine Eliminate this Scourge in Papua New Guinea?
Anne Lanham, Lillian Mwanri

We have released issues of some journals on February 2013.
American Journal of Public Health Research
American Journal of Medical Sciences and Medicine
American Journal of Medical and Biological Research
American Journal of Pharmacological Sciences
American Journal of Clinical Medicine Research
American Journal of Nursing Research
American Journal of Cancer Prevention
American Journal of Medicine Studies
American Journal of Infectious Diseases and Microbiology
American Journal of Cardiovascular Disease Research
American Journal of Biomedical Research
American Journal of Mechanical Engineering
American Journal of Microbiological Research
Journal of Preventive Medicine
American Journal of Food and Nutrition
American Journal of Hypertension Research
American Journal of Sports Science and Medicine
Journal of Cancer Research and Treatment
American Journal of Zoological Research
Journal of Biomedical Engineering and Technology
American Journal of Microbiological Research
Biomedical Science and Engineering

We are pleased to announce that submissions are now being accepted for peer review for all the journals across all our subject areas in SciEP.

Please submit your manuscript via our online submission system:
http://www.sciepub.com/author/signin

To unsubscribe from our mailing list, please click on the following link: unsubscribe

I am looking forward to hearing from you.

Kind regards,

David Rain
Email:join@sciepub.com
Science and Education Publishing (http://www.sciepub.com)

Label_Title

Dear Label_Name,

Greetings! I hope you are well.

I am writing on behalf of an international publishing house, Science and Education Publishing, USA (http://www.sciepub.com).

Science and Education Publishing (SciEP) is a multidisciplinary open access publisher of Journals covering the fields of Science, Technology and Medicine. All SciEP publications are subject to high-quality peer review, editorial and production processes and are freely available online.

Welcome to the April, 2013 edition of SciEP newsletter, providing monthly summaries of articles on science & education related topics of interest to scientist and professionals. The mission of our journals is to provide an open access forum for publishing new findings on issues pertinent to scientific and academic field. We also invite you to submit original research papers, review articles, short reports, or case studies are considered for publication in our Multidisciplinary Journals.

American Journal of Public Health Research
DOI: 10.12691/ajphr-1-1-3

The Implementation of a Tele-Homecare System with Service Oriented Architecture and HL7 Message Transmission Standard
Ching-Sung Wang

American Journal of Medical and Biological Research
DOI: 10.12691/ajmbr-1-1-2

The Influence of Ethanol on Pyruvate Kinases Activity in Vivo, in Vitro, in Silico
Lelevich Sergey Vladimirovich, Khrustalev Vladislav Victorovich, Barkovsky Eugene Victorovich, Shedogubova Tatyana Aleksandrovna

American Journal of Medical Sciences and Medicine
DOI: 10.12691/ajmsm-1-1-1

Clinical and Histological Features in Wegener Granulomatosis
Li Cavoli Gioacchino, Passantino Rita, Bono Luisa, Tortorici Calogera, Ferrantelli Angelo, Giammarresi Carlo, Rotolo Ugo

American Journal of Infectious Diseases and Microbiology
DOI: 10.12691/ajidm-1-1-2

The Curse of Lymphatic Filariasis: Would the Continual Use of Diethylcarbamazine Eliminate this Scourge in Papua New Guinea?
Anne Lanham, Lillian Mwanri

We have released issues of some journals on February 2013.
American Journal of Public Health Research
American Journal of Medical Sciences and Medicine
American Journal of Medical and Biological Research
American Journal of Pharmacological Sciences
American Journal of Clinical Medicine Research
American Journal of Nursing Research
American Journal of Cancer Prevention
American Journal of Medicine Studies
American Journal of Infectious Diseases and Microbiology
American Journal of Cardiovascular Disease Research
American Journal of Biomedical Research
American Journal of Mechanical Engineering
American Journal of Microbiological Research
Journal of Preventive Medicine
American Journal of Food and Nutrition
American Journal of Hypertension Research
American Journal of Sports Science and Medicine
Journal of Cancer Research and Treatment
American Journal of Zoological Research
Journal of Biomedical Engineering and Technology
American Journal of Microbiological Research
Biomedical Science and Engineering

We are pleased to announce that submissions are now being accepted for peer review for all the journals across all our subject areas in SciEP.

Please submit your manuscript via our online submission system:
http://www.sciepub.com/author/signin

To unsubscribe from our mailing list, please click on the following link: unsubscribe

I am looking forward to hearing from you.

Kind regards,

David Rain
Email:join@sciepub.com
Science and Education Publishing (http://www.sciepub.com)

Comparative Thermal Performance Analysis of Beam-and-Block Floor Systems Using Typha australis Earth Blocks and Conventional Concrete Blocks in Hot Semi-Arid Climates

Babacar Diouf*, Bator CISSE, Mariama BA, Kadia Thilly, Cheikh Tidiane Seck

Institut Polytechnique de Saint-Louis (IPSL), Université Gaston Berger, Saint-Louis, Senegal

Abstract: The building sector in Senegal faces significant energy and thermal comfort challenges, with approximately 60% of residential energy consumption devoted to cooling in a hot semi-arid climate where urban temperatures regularly exceed 35–40°C. Conventional construction materials such as concrete exhibit high thermal conductivity (typically >1.4 W m⁻¹K⁻¹), exacerbating indoor heat gain. This study presents a quantitative comparative analysis of the thermal performance of two beam-and-block floor assemblies: one incorporating Typha australis–earth hollow blocks and insulating panels, and a reference assembly using standard concrete hollow blocks. Steady-state thermal conduction calculations were performed in accordance with ISO 6946 and ADEME guidelines on multi-layer floor systems. Results demonstrate that the typha-based floor achieves a total thermal resistance of Rth = 2.932 K m² W⁻¹ and a thermal transmittance of U = 0.341 W m⁻² K⁻¹, compared to Rth = 0.197 K m² W⁻¹ and U = 5.076 W m⁻² K⁻¹ for the concrete counterpart. The total heat flux through the typha floor (733.37 W for a 215 m² surface) is approximately 13 times lower than that of the concrete floor (9822.06 W). These findings confirm Typha australis as a high-potential bio-sourced insulating material suitable for sustainable bioclimatic construction in West Africa, capable of substantially reducing cooling energy demand while supporting local circular economies.

Keywords: Bio-sourced materials, Thermal insulation, Beam-and-block floor, Typha australis, Thermal transmittance, Bioclimatic architecture, Senegal, Hot climate

Received April 13, 2026; Revised May 15, 2026; Accepted May 22, 2026

Citation: Babacar Diouf, Bator CISSE, Mariama BA, Kadia Thilly, Cheikh Tidiane Seck, Comparative Thermal Performance Analysis of Beam-and-Block Floor Systems Using Typha australis Earth Blocks and Conventional Concrete Blocks in Hot Semi-Arid Climates. American Journal of Civil Engineering and Architecture, 14 (3). 112-116. January 2026. doi:10.12691/ajcea-14-3-3

1. Introduction

The construction sector in Senegal accounts for approximately 41.3% of national final energy consumption, with electricity use projected to represent 70% of building energy demand by 2030 [1]. In urban contexts, air conditioning driven by poor thermal building envelopes constitutes the dominant driver of this demand, particularly during the dry season when outdoor temperatures regularly surpass 40°C [2]. The challenge of reducing cooling loads while improving occupant thermal comfort calls for a re-examination of conventional construction practices and materials.

Conventional hollow concrete blocks, the standard infill element in beam-and-block floor systems widely used across West Africa, exhibit thermal conductivity values typically ranging from 1.4 to 2.0 W m⁻¹K⁻¹ [3]. These high values result in significant heat transmission through floor assemblies, particularly in terraced rooftop floors directly exposed to solar radiation. As a consequence, occupants of such buildings experience pronounced thermal discomfort and incur elevated energy costs for mechanical cooling.

Typha australis (common cattail) is a perennial aquatic macrophyte found extensively in the wetlands of the Senegal River valley. More than 100,000 hectares of agricultural land have been colonised by the plant, causing significant ecological and economic disruptions [4]. Its valorisation as a construction material therefore presents a dual opportunity: ecological control of its invasive spread and substitution of energy-intensive conventional materials.

A growing body of literature demonstrates that Typha australis possesses thermal conductivity values ranging from 0.032 to 0.055 W m⁻¹K⁻¹ for bulk densities between 30 and 80 kg m⁻³, values comparable to or lower than commercial synthetic insulants [5,6]. When incorporated into earth-based composites to produce hollow floor blocks (hourdis), the resulting material retains insulating properties while also providing acceptable structural performance [7,8].

Despite these promising material-level results, quantitative analyses of full floor assembly thermal performance under realistic Sahelian climatic boundary conditions remain scarce. This paper addresses this gap by performing steady-state thermal conduction analyses on two complete beam-and-block floor assemblies—one integrating typha-earth hollow blocks and insulating typha panels, the other using conventional concrete hollow blocks—and rigorously comparing their total thermal resistances, transmittance coefficients, heat flux densities and total heat flows.

2. Background and Related Work

2.1. Typha Australis as a Construction Material

Typha australis is a monocotyledonous perennial plant that thrives in shallow freshwater environments at depths not exceeding 1.5 m. It can attain heights of 3.5–4.0 m, with linear leaves 1–2 cm wide and stem sections characterised by a round cross-section and high axial compressive strength [4]. The plant's leaves consist of porous aerated parenchyma (aerenchyme) with thermal conductivity as low as 0.032 W m⁻¹K⁻¹, attributed to the trapped air network within the cellular microstructure [5].

Chemical composition studies (Duke, 1983; Theuerkorn, 2001) indicate that Typha leaves contain 30–39% crude fibres, 38–48% carbohydrates, and 7–12% crude protein in dry matter, with significant cellulose and lignin fractions that contribute to fire resistance. The mechanical behaviour is anisotropic: longitudinal compressive resistance reaches approximately 1 N mm⁻¹, while transverse response is highly elastic [9].

Building applications of Typha include ligature-bound panels, woven mats, thatched roofing elements, compressed loose-fill, earth-typha bricks, earth-typha plasters, and hollow floor blocks. The latter—hourdis terre-typha—are fabricated by moulding an earthen slurry mixed with shredded Typha fibres and allowing air curing. Manufacturer data sheets report thermal conductivity of 0.12–0.15 W m⁻¹K⁻¹ for bulk-density blends of 600–610 kg m⁻³ [10].

2.2. Thermal Performance of Bio-Sourced Floor Systems

Study [11] demonstrated that incorporating Typha fibres into cement matrices reduced thermal conductivity from 1.08 W m⁻¹K⁻¹ to 0.52 W m⁻¹K⁻¹, while [12] reported conductivities of 0.085–0.22 W m⁻¹K⁻¹ for Typha-based insulating panels. Studies on composites of Typha with recycled lime showed mechanical compressive strengths of 1.34–2.30 MPa with conductivities of 0.078–0.192 W m⁻¹K⁻¹ [8]. Thermomechanical characterisation of Typha particleboards with arabic gum binders yielded conductivities of 0.055–0.083 W m⁻¹K⁻¹ [13].

At the building system level, experimental campaigns carried out under the TyCCAO and PEEB programmes have confirmed that Typha-integrated envelopes reduce cooling energy demand by up to 25% relative to conventional concrete structures [2,14]. However, published analyses rarely address the full floor assembly thermal performance in a standardised, reproducible framework applicable to engineering practice.

3. Materials and Floor Assembly Descriptions

3.1. Typha-Earth Floor Assembly

The typha-based floor is a six-layer beam-and-block assembly representative of current bioclimatic practice in Senegal. From soffit to surface, the layers are: (1) typha-earth hollow blocks (hourdis) serving as permanent formwork between pre-stressed concrete joists; (2) a reinforced concrete compression slab; (3) insulating typha-fibre panels; (4) a waterproofing membrane; (5) a cement mortar screed; and (6) fired-ceramic floor tiles. Physical and thermal characteristics of each layer were sourced from manufacturer technical data sheets and published experimental literature, as summarised in Table 1.

Table 1. Thermal properties of the typha-based floor assembly layers

3.2. Conventional Concrete Floor Assembly (Reference)

The reference floor consists of five layers: (1) standard concrete hollow blocks; (2) a reinforced concrete compression slab; (3) a waterproofing membrane; (4) a cement mortar screed; and (5) ceramic tiles. No additional insulation layer is included, as this configuration is representative of standard construction practice in Senegal. Table 2 presents the layer characteristics.

Table 2. Thermal properties of the reference concrete floor assembly layers

4. Methodology

4.1. Theoretical Framework

Thermal calculations were performed under the steady-state, one-dimensional heat conduction hypothesis as standardised in ISO 6946:2017 [15] and consistent with ADEME energy performance guidelines [16]. This approach is appropriate for comparative performance evaluation across two alternative assemblies under identical boundary conditions and is widely applied in regulatory energy calculations for buildings.

The following simplifying assumptions were adopted: (i) steady-state thermal regime with time-invariant interior and exterior temperatures; (ii) perfect thermal contact between adjacent layers (no interfacial resistance); (iii) homogeneous and isotropic material properties within each layer; (iv) one-dimensional heat transfer perpendicular to the floor plane, neglecting edge effects; and (v) no internal moisture migration or convection within the floor system.

4.2. Governing Equations

For each homogeneous layer i, the thermal resistance Ri (K m² W⁻¹) is given by Fourier's law:

[picture] | (1)

where eᵢ is the layer thickness (m) and λᵢ its thermal conductivity (W m⁻¹K⁻¹). The total thermal resistance of the floor is the sum of individual layer resistances:

[picture] | (2)

The thermal transmittance (U-value, W m⁻²K⁻¹) is the reciprocal of total thermal resistance:

[picture] | (3)

The heat flux density φ (W m⁻²) through the floor is:

[picture] | (4)

where ΔT is the temperature difference between indoor and outdoor environments. The total heat flow Φ (W) for a floor of surface area S (m²) is:

[picture] | (5)

4.3. Boundary Conditions

Boundary conditions were set to represent peak summer conditions in the Senegal River valley. The outdoor (top surface) temperature was set at 35°C, consistent with recorded average maximum dry-bulb temperatures during the hot dry season in Saint-Louis, Senegal [2]. The indoor (soffit) temperature was set at 26°C, corresponding to an acceptable thermal comfort threshold in naturally ventilated spaces in tropical climates [17]. This yields a temperature differential of ΔT = 9 K. The total floor surface area considered in this study is 215 m², corresponding to the project building under study.

5. Results

5.1. Layer-by-Layer Thermal Resistances – Typha Assembly

The individual thermal resistances computed for each layer of the typha-based floor are detailed in Table 3. The distribution reveals a strongly stratified contribution: the two typha-containing layers (hollow blocks and insulating panels) account for 96.4% of the total resistance, while the remaining four layers contribute only 3.6%. This highlights the dominant role of the bio-sourced elements in the overall thermal performance.

Table 3. Layer thermal resistances for the typha floor assembly

5.2. Comparative Results

Table 4 presents the key thermal performance indicators for both floor assemblies, together with the absolute and relative differences between the two systems.

Table 4. Comparative thermal performance indicators for the two floor assemblies (ΔT = 9 K, S = 215 m²)

6. Discussion

The results demonstrate an unambiguous and quantitatively substantial improvement in thermal resistance when Typha australis-based elements replace conventional concrete hollow blocks. The typha floor assembly achieves a U-value of 0.341 W m⁻²K⁻¹, which is 14.9 times lower than that of the concrete reference (5.076 W m⁻²K⁻¹). This performance is attributable principally to the exceptionally low thermal conductivity of Typha australis (λ = 0.032–0.055 W m⁻¹K⁻¹), arising from the highly porous, aerenchymatous microstructure of its leaf tissue [5], and to the combined action of the hollow blocks (λ = 0.15 W m⁻¹K⁻¹) and the supplementary insulating panel (λ = 0.055 W m⁻¹K⁻¹).

From an energy performance perspective, the total heat flow reduction from 9822 W to 733 W represents a decrease of approximately 92.5% for a floor area of 215 m² under peak summer conditions. On an annual basis, assuming 200 daily peak hours of differential exposure, this corresponds to a cooling load reduction on the order of 1.9 MWh per year for this floor alone—a significant contribution to building energy efficiency in a country where 70% of building electricity is anticipated to derive from cooling by 2030 [1].

The U-value obtained for the typha assembly (0.341 W m⁻²K⁻¹) is consistent with the range reported for bio-sourced insulated floor systems in other tropical and subtropical contexts. Diaw et al. [11] and Gassama et al. [12] both documented significant reductions in heat transfer for typha composites, while Adama et al. [7] confirmed the viability of clay-typha composites with thermal conductivities between 0.078 and 0.192 W m⁻¹K⁻¹. The present study extends these findings from the material level to the full building assembly level under defined climatic boundary conditions, providing engineering-grade data for design practice.

The concrete floor U-value of 5.076 W m⁻²K⁻¹ is in accordance with literature values for uninsulated concrete floor slabs, confirming that the reference assembly is representative of typical Senegalese practice where thermal insulation in floors remains uncommon [2].

Beyond thermal performance, Typha-based hollow blocks offer a mass density of 600–610 kg m⁻³ compared with 2400 kg m⁻³ for concrete, reducing permanent floor dead load by approximately 75% for the hollow block component. This reduction decreases the structural design actions on beams, columns and foundations, potentially enabling more economical structural dimensioning and reduced cement and steel consumption.

From an environmental perspective, Typha australis requires no industrial processing energy for the raw material phase; transformation (harvesting, drying, shredding, moulding) is largely artisanal or semi-industrial, resulting in a far lower embodied energy per unit volume than concrete [14]. Furthermore, as a photosynthetically active biomass, Typha sequesters atmospheric CO₂ during growth, offering partial carbon sink benefits within a bio-based construction strategy. These characteristics align with the sustainability objectives of Senegal's PSE (Plan Sénégal Émergent) and the targets of the PNEEB (Programme National pour l'Efficacité Énergétique dans le Bâtiment).

7. Conclusion

This study has provided a rigorous quantitative comparison of the thermal performance of a Typha australis-earth beam-and-block floor assembly against a conventional concrete counterpart, applying steady-state thermal conduction analysis in accordance with ISO 6946 under representative Sahelian boundary conditions. The main findings are:

(i) The typha floor assembly achieves a total thermal resistance of 2.932 K m² W⁻¹ and a transmittance of 0.341 W m⁻²K⁻¹, representing improvements of approximately 14.9 times over the concrete reference assembly (Rₜₕ = 0.197 K m² W⁻¹; U = 5.076 W m⁻²K⁻¹).

(ii) Total heat flow through the 215 m² typha floor under peak summer conditions (733.37 W) is 13.4 times lower than that through the concrete floor (9822.06 W), corresponding to an estimated annual cooling load reduction of approximately 1.9 MWh.

(iii) The two typha-based layers (hollow blocks and insulating panels) contribute 96.4% of the total thermal resistance, confirming the decisive role of bio-sourced elements in floor system thermal performance.

These results establish a quantitative engineering basis for the integration of Typha australis-based floor systems into bioclimatic building practice in Senegal and comparable West African contexts. The material simultaneously addresses thermal, structural, environmental and socio-economic objectives, supporting local value chains in rural areas while contributing to national energy efficiency targets. The authors recommend the development of standardised technical specifications, long-term durability testing protocols, and dynamic energy simulation studies to accelerate the adoption of typha-based floor systems at scale.

ACKNOWLEDGEMENTS

The authors thank the staff of Atelier Kemit Architectes (AKA), M. Ernest Dione (PNEEB/Typha Programme), This work was supported by the Institut Polytechnique de Saint-Louis and carried out in the framework of the final-year engineering thesis programme.

References

[1]   | Adama G., Diouf B., Ly E.B., Moise M., Diène N. Caractérisation des propriétés mécaniques et thermiques de matériaux à base de ciment, de Typha Domingénis et d'argile. J. Phys. SOAPHYS. 2023; 3(2): 1–6.
[2]   | Sow E.M., Gassama D., Diagne M., Seck A. Bâtiment et énergie: Analyse du secteur du bâtiment au Sénégal—Synthèse et recommandations. PEEB Programme; June 2021. Available: https:// peeb.build/wp-content/ uploads/ 2024/ 12/ Synthese_ Batiment_et _energie_Senegal_PEEB.pdf.
[3]   | Dıeye, Younouss, Pape M. Toure, Seckou Bodıan, Prince M. Gueye, Mactar Faye, and Vincent Sambou. 2021. “Study of Thermal and Mechanical Properties of Typha Leaf - Clay Panels”. Journal of Sustainable Construction Materials and Technologies 6 (4): 135-42.
[4]   | Tarus, Bethwel Kipchirchir, et al. "Valorisation of cattail (Typha) biomass: Fibre extraction, properties, and applications in sustainable material systems." Bioresource Technology Reports (2026): 102570.
[5]   | Samin E. CRATerre: Rapport technique de capitalisation des résultats de la R&D à mi-parcours. Grenoble: CRATerre; December 2015.
[6]   | Vėjelienė J. Processed straw as effective thermal insulation for building envelope constructions. Eng. Struct. Technol. 2012; 4(3): 96–103.
[7]   | Elhaj-Maham, El Moustapha, et al. "Study of the Physic-Mechanical Properties of a Typha Concrete Composites: A Possible New Material for Sustainable Construction." Materials Science Forum. Vol. 1122. Trans Tech Publications Ltd, 2024.
[8]   | Diaw I., Faye M., Hans S., Sallet F., Sambou V. Valorization of recovered lime in cement-Typha concretes: thermal and mechanical behavior. In: Innovations and Interdisciplinary Solutions for Underserved Areas. Cham: Springer; 2022. p. 267–276.
[9]   | Rakotomalala L., Misse A. CRATerre rapport technique: identification du contexte sénégalais. Grenoble: CRATerre; December 2014.
[10]   | Élémenterre. Fiche technique: Hourdis Terre Typha. Paris: Élémenterre; 2023.
[11]   | Diaw I., Faye M., Hans S., Sambou V. Thermal conductivity of cement-Typha composites. Mater. Lett. 2021; 289: 129383.
[12]   | Laaouar, Boutahar, et al. "Assessment of Thermophysical Properties of Typha Fiber Insulation Panels for Sustainable Buildings." E3S Web of Conferences. Vol. 680. EDP Sciences, 2025.
[13]   | Vejeliene J., Gailius A., Vejelis S., Vaitkus S., Keriene J. Thermomechanical characterization of particleboards from powder Typha leaves. J. Civ. Eng. Manag. 2011; 17(4): 489–496.
[14]   | Theuerkorn W., Henning R.K. Le Typha australis: menace ou richesse? Eschborn: GTZ; 2002.
[15]   | ISO 6946:2017. Building components and building elements—Thermal resistance and thermal transmittance—Calculation methods. Geneva: International Organization for Standardization; 2017.
[16]   | ADEME. Méthode de calcul de la résistance et de la conductance thermiques. Paris; 2016.
[17]   | Fanger P.O. Thermal Comfort: Analysis and Applications in Environmental Engineering. Copenhagen: Danish Technical Press; 1970.